Free shipping method on this item is USPS Priority Mail
Great Plains Industries, INC EZ-8RV Fuel Pump
No mounting bracket
This pump is not intended to be used with an automatic nozzle.
This pump is designed for use only with gasoline (up to 15% alcohol blends such as E15), diesel fuel (up to 20% biodiesel blends such as B20) and kerosene.
DO NOT use this pump for dispensing any fluids other than those for which it was designed. To do so may damage pump components and will void the warranty.
Designed to operate on a typical 12-volt DC automotive electrical system.
This pump is designed to self-prime with dry gears.
You can wire a switch on the power line, but there is no switch on this model of pump.
Have a certified technician install all parts to prevent product damage and personal injury.
Do not leave the system running without fluid.
"Dry running" can damage the pump. If the system fails to deliver fuel after 15 to 20 seconds, turn the system off and refer to the Troubleshooting Section in manual.
Do not pump the tank completely dry, as contaminants from the bottom of the tank may enter the pump.
Excessive motor heat can trip the device. It resets automatically after the motor has cooled.
Make sure all threaded fuel connections are wrapped with three to four turns of Teflon tape or pipe thread sealant approved for use with petroleum fuels.
Clean the tank interior of all dirt and debris. Make sure the tank is vented. A vent cap rated at 3 psi or less is recommended.
Suction line design and size is important for optimum pump performance. GPI requires suction line to be 3/8" minimum diameter.
Pump must be mounted within the clearance lines of the vehicle and protected from road impact damage.
A grounding connection is provided. It is identified as a green colored binding head screw in the electrical cavity. Connect these pumps only to a 12- volt DC power supply.
DO NOT attempt connection to a 24-volt DC, 115-volt AC or 230 volt AC power source.
For installation in unclassified ares a flexible power cord, fuse and strain relief grip should be used.
NOTE These components have NOT been evaluated as part of the UL Listed Equipment and are not intended for use in a Hazardous (Classified) Location.